BLOW-OFF DRAIN VALVE f TWO-PIECE BALL VALVE WOG 600 f BRONZE f MALE x FEMALETHREADED ENDS
TITAN FLOW CONTROL, INC. ® TITAN
BV 60-BZ ( ca s t bronze )
S IZE RANGE : 1 / 4" ~ 2"
full port flow ful l port de s i gn of f e r s comp l e t e and rap i d cl ean i ng of s tra i ne r scr e en wi th m i n i mal p r e s sur e drop . s imple operat ion qu i ck quart e r turn op ens or clos e s valv e . lock i ng handl e i s al so ava i lab l e . s d i rect connect ion to stra iner mal e thr eaded ends mount d i r ect ly i nto s tra i ne r b low - of f connect i on for conv en i ent b low down cl ean i ng . s
PRESSURE/ TEMPERATURE RATING BRONZE ASTM B62
s factory installat ion as blow - off valve b al l valv e can b e p rof e s s i onal ly i ns tal l ed to a t i tan s tra i ne r at our factory , ensur i ng qual i ty and r educ i ng sh i p p i ng and labor cos t s .
rugged , high qual i ty des ign the bv 60 f eatur e s a chrom i um p lat ed b al l , r e i nforced - p t f e s eat , and b low - out p roof s t em de s i gn .
R-PTFE: -100 °F - 400 °F
1. The above listed temperatures are theoretical and may vary during actual operating conditions.
can be professionally installed at the titan factory !
screen cleaning : during normal use , the strainer screen will become clogged with foreign matter causing the differential pressure to increase . once the differential pressure has reached an unacceptable value , blow - down cleaning is recommended . it is not advisable to allow the differential pressure to increase by 20 psi as this may cause the screen to fail and possibly damage downstream equipment . if the differential pressure is not restored to normal parameters after blow - down cleaning then the screen must be removed and cleaned or replaced .
The above data represents common market and service applications. No representation or guarantee, expressed or implied, is given due to the numerous variations of concentrations, temperatures and flow conditions that may occur during actual service.
YOUR PIPELINE TO THE FUTURE! TITAN FLOW CONTROL, INC.
Fax: 910-738-3848 s email@example.com s www.titanfci.com